Whoop’s Turn Key Advantage:
1). FCC Certified Engineers
2). Calibrated Spectrum Analyzers Recognized Nationally as the Standard
3). In-House Design
4). On-Site Field Engineers
5). Certified Electricians
Whoop’s 24 Point Compliance Program:
1). System must provide a minimum of -95 dB signal strength throughout 95% of the building.
2). System must provide a minimum of -95 dB signal strength within 99% of all critical areas.
3). System requires a 20A dedicated circuit.
4). Back up power source required is 4-hours at 100% capacity.
5). Amplifier will be monitored by fire alarm panel.
6). Battery back up will be monitored by fire alarm panel.
7). Amplifier & battery back up will be housed in a NEMA 4 type enclosure.
8). Repeater will be FCC Certified.
9). Repeater shall be capable of analog & digital modes.
10). Entire system shall be capable of future upgrades.
11). Repeater shall be class A or class B depending on AHJ requirements.
12). Room containing repeater & battery back up must be fire rated for 2-hours.
13). Room containing repeater & battery back up must be mechanically ventilated.
14). Room containing repeater & battery back up must be have a smoke detector.
15). Riser cable run must have level 2 survivability.
16). System integration will be overseen by FCC General Radio Operator License (GROL) holder.
17). Isolation between donor antenna and service antenna’s gain will exceed 20 dB.
18). Amplifier & battery backup are UL Listed
19). Site survey shall be a 20-point grid test performed by licensed FCC G.R.O.L. holder.
20). All horizontal cabling must be plenum rated
21). All horizontal cabling must be of type air dielectric (heliax)
22). All horizontal cabling and splitters/couplers must be mechanically protected within EMT conduit.
23). Roof antenna must be tied into lighting protection of building.
24). Permit plans are to be stamped by state certified project engineer.